Remeha hot water heat pump Azorra Ace 250 liters 2.4 kW

2025-04-16T12:24:03+02:00

Vendor: Remeha
Type: Hot water heat pump
Price: 2849.00

Remeha hot water heat pump 2.4 kW

Air/water hot water heat pump 2.4 kW

Azorra Ace 250 liters 2.4 kW

Air-to-water heat pumps are frequently used. These extract heat from the ambient air and use it inside the building to heat water. This makes it possible to heat domestic hot water and operate radiators or underfloor heating.

Air/water heat pump with 250 liter storage capacity

Operating range from -7 to +42°C ambient temperature

Removable controller with clock program for three switching times per day and legionella protection circuit

Active climate protection with high CO² savings and possible connection to a PV system

Water comfort for 4-6 person households

Hot water preparation with short heating time up to 65°C

Designed to meet renovation needs

Quick and cost-effective installation

Modern control platform with 4 different operating modes

The domestic water pump can be transported horizontally.

The supply and exhaust air can be routed directly through indoor spaces or through outdoor air.

Durable storage container made of enamelled sheet steel with corrosion protection via impressed current anode.

built-in electric insert with 1.8 kW

COP = 3.63 at air temperature 15 °C and water temperature 10 °C

Installation and connection of the Azorra Ace heat pump:

Compact size (710mm x 670mm x 1760mm (250L))

Easy to install thanks to useful carrying handles.

Delivered fully assembled -> easy installation

The cooled exhaust air can z.B. The air can be directed into a storage room or wine cellar, thus providing free cooling. If the supply and exhaust air from the room is used, the heat pump also dehumidifies the room.

Hydraulic connections all accessible from one side

Solar thermal energy can be connected via the integrated heat exchanger. This transforms the domestic hot water heat pump into a true solar storage system with energy-efficient storage charging support. The heat pump can be connected to the outside air from above via a Ø160 air duct (EPP/EPE or galvanized steel).> Any direction is possible without collision.

Azorra Ace regulation

4 possible operating modes:

Automatic: Hot water is supplied via the heat pump and, if necessary, the additional safety heating element is switched on, or the additional heat exchanger of the Azorra Ace is used.

Eco: Hot water is supplied exclusively via the heat pump.

Boost: Rapid heating with all 3 possible heat generators (heat pump, electric heating element, external heat generator)

Holidays: Hot water frost protection down to 10°C during extended absences. Furthermore, operating hours counter, night-time electricity optimization, and programmable hot water heating are included.

The control unit is removable and can be attached anywhere in the room. The hot water heat pump is connected to the control system via a 2-wire bus cable.

Technical data

Maximum electrical energy consumption: 2,480 W

Min/Max electrical energy consumption of heat pump: 440/680 W

Electric heating element power: 1,800 W

Min/Max operating limits for supply air: -7/42 °C

Max Temp.Heat pump only/with electric auxiliary heating: 65/75 °C

Maximum operating pressure: 8 bar

Supply voltage: 230V/50Hz

Circuit breaker: 16 A

Electrical protection class: IP X1B

Sacrificial anode: TAS

Cold and hot water connections: 3/4"

Storage material: Enamelled steel conforming to DIN 4753

Insulation thickness: 50 mm

Air connection diameter: 160 mm

Maximum air duct length: 20 m

Connection for smooth tube heat exchanger: 3/4"

Heat exchanger surface area: 0.93 m²

Refrigerant/Quantity: R290/0.150 kg

GWP: 3

CO2 equivalent: 0

Sound power level indoor/outdoor: 49/58 dB(A)

Sound pressure level (2m): 35 dB(A)

Empty weight: 113 kg

Dimensions (H x W x D): 1760/666/705 mm

Energy efficiency class: A+

Download

Product data sheet

brochure

Assembly.- & User manual